Have a question, comment, or request? Send us a message!
Hours: 8:00am - 5:00pm CDT
13723 Riverport Drive
St. Louis, MO 63043
1609 Park 370 Place
St. Louis, MO 63042
We are excited to introduce our new training hub, Potter Academy. Through Potter Academy, you will be able to access hundreds of bite sized self-paced training modules, earn CEUs, and deepen your industry and product knowledge – all for free!
Potter Announces Integrated Voice Systems
Announcing the release of Potter's Integrated Voice System along with the IPA-4000V and AFC-1000V fire alarm …
Potter Receives Gold Awards For Integrated Voice Systems
Potter Electric Signal Company, LLC is proud to announce a Gold-level win at the 2022 Government Security …
What People Are Saying About Working With Potter
The Model VSR-S is a vane type waterflow switch for use on wet sprinkler systems that use 1" (25mm), 1¼" (32mm), 1½" (38mm) or 2" (50mm) pipe size. The unit may also be used as a sectional waterflow detector on large systems.
Codes and Approvals
Small Pipe Waterflow Alarm Vane Switches: UL Listed waterflow alarm switches shall be furnished and installed at each sprinkler system branch line connection to the wet pipe main where indicated on the drawings, and as required by NFPA Standards. Mounting shall be by means of a 1 inch TEE fitting installed in the branch line. Vanes shall be field installed on the switch from a selection supplied with the switch and fit pipe sizes 1 inch through 2 inches. Waterflow switches shall be capable of operation in system pressures up to 300 PSI, maximum surges of up to 18 FPS and alarm activation at 10 GPM. Switch configuration shall consist of two sets of single pole double throw (S.P.D.T.) Form C synchronized sets of contacts rated at 10A, 125 VAC and 2A, 30 VDC. Switch enclosure shall meet NEMA 4 rating and shall be equipped with an instantly recycling adjustable retard with a 0-90 second range. Enclosure cover shall be held captive by tamper resistant screws or supervised for removal by a cover tamper switch. Waterflow alarm vane switch shall be Model VSR-S manufactured by Potter Electric Signal Company.
Additional Information for Engineers:
If there is a shut off valve in line with the VSR-S it should be monitored. Closing this valve can prevent an alarm.
Click here to view the VSR-S datasheet.
To view updated tracking on your order, please enter your customer purchase order number.
Please allow at least 24 hours from the time of order for shipping information to be available. For more information or questions about tracking, contact customer service at 800-325-3936.