Have a question, comment, or request? Send us a message!
Hours: 8:00am - 5:00pm CDT
13723 Riverport Drive
St. Louis, MO 63043
1609 Park 370 Place
St. Louis, MO 63042
Potter Announces SignaLink™ Bridge Wireless Supervisory System
Potter Electric Signal Company, LLC of St. Louis, Missouri USA, announces the release of the SignaLink Bridge …
Potter Peer to Peer Fire Alarm Systems Win Product of the Year
Potter Electric Signal Company is proud to announce a victory for its Peer to Peer Networking Cards at the …
What People Are Saying About Working With Potter
The Potter PS40-EX Supervisory Pressure Actuated Switch is designed primarily to detect an increase and/or decrease from normal system pressure in automatic fire sprinkler systems located in hazardous locations classified as shown above. Typical applications are: Dry pipe systems, pre-action air/nitrogen supervision, pressure tanks, air supplies, and water supplies. The PS40-EX switch is factory set for 40 PSI (2,8 BAR) normal system pressure. The switch marked with the word LOW is set to operate at a pressure decrease of 10 PSI (7 BAR) at 30 PSI (2,1 BAR). The switch marked with the word HIGH is set to operate at a pressure increase of 10 PSI (7 BAR) at 50 PSI (3,5 BAR).
The Potter PS10-EX Pressure Actuated Switch is designed for the detection of a waterflow condition in automatic fire sprinkler systems located in hazardous locations classified as shown above. Typical applications are: Wet pipe systems with alarm check valves, dry pipe, preaction, or deluge valves. The PS10-EX is also suitable to provide a low pressure supervisory signal; adjustable between 4 and 20 psi (0,27 and 1,3 BAR).
Codes and Approvals
Waterflow Alarm Pressure Switch For Use In Hazardous Locations: UL Listed/FM Approved waterflow alarm pressure switch shall be furnished and installed at each sprinkler system connection to the dry pipe alarm port where indicated on the drawings, and as required by NFPA Standards. Waterflow pressure switch shall be capable of operation in system pressures up to 250 PSI, and shall operate on increasing pressure at the alarm port to 6 PSI. Switch configuration shall consist of two sets of single pole double throw (S.P.D.T.) Form C synchronized sets of contacts rated at 15A, 125 VAC and 2A, 24 VDC. The switch shall employ independent pressure elements for each switch. Switch enclosure shall be suitable for use in Class I Division 1 & 2 Groups B, C, D, Class II Division 1 & 2 Groups E, F, G, Class III Division 1 & 2 and the cover shall be held captive by tamper resistant screws or supervised for removal by a cover tamper switch. Pressure connection to the system shall be via 1/2 inch male NPT. All in line valves shall be electrically supervised for their fully open position. Waterflow alarm pressure switch shall be Model PS10-EX manufac¬tured by Potter Electric Signal Company.
Click here to view more info about the PS10-EX
Click here to view more info about the PS40-EX
To view updated tracking on your order, please enter your customer purchase order number.
Please allow at least 24 hours from the time of order for shipping information to be available. For more information or questions about tracking, contact customer service at 800-325-3936.