Have a question, comment, or request? Send us a message!
Hours: 8:00am - 5:00pm CDT
13723 Riverport Drive
St. Louis, MO 63043
1609 Park 370 Place
St. Louis, MO 63042
Potter Announces SignaLink™ Bridge Wireless Supervisory System
Potter Electric Signal Company, LLC of St. Louis, Missouri USA, announces the release of the SignaLink Bridge …
Potter Peer to Peer Fire Alarm Systems Win Product of the Year
Potter Electric Signal Company is proud to announce a victory for its Peer to Peer Networking Cards at the …
What People Are Saying About Working With Potter
The Model VS-SP is a vane type waterflow switch for use on wet sprinkler systems. These devices may be used as sectional flow indicators on large sprinkler systems and on smaller sprinkler systems such as mobile homes and residential dwellings.
The VS-SP does not have a retard to prevent false alarms due to water surges. Therefore it should NOT be used on systems with variable water pressure supplies except in the case of elevator recall.
Codes and Approvals
Special Application Vant Type Waterflow Alarm Switches: UL, cUL Listed and CE Marked waterflow alarm switches shall be furnished and installed at each sprinkler system branch line connection to the wet pipe main where indicated on the drawings, and as required by NFPA Standards. Mounting shall be by means of a 1 inch TEE fitting installed in the branch line. Vanes shall be field installed on the switch from a selection supplied with the switch and fit pipe sizes 1 inch through 2 inches. Waterflow switches shall be capable of operation in system pressures up to 250 PSI, maximum surges of up to 18 FPS and alarm activation at 10 GPM. Switch configuration shall consist of one single pole double throw (S.P.D.T.) Form C set of contacts rated at 15A, 125 VAC and 2.5A, 30 VDC. It shall be possible to field install an optional second set of switch contacts. Flowswitch enclosure shall meet NEMA 4 rating and shall be held captive by tamper resistant screws or supervised for removal by a cover tamper switch. Connection to piping shall be by means of 1” NPT or 1” BSPT threaded brass bushing. Waterflow alarm vane switch shall be Model VS-SP for NPT threads or VS-SPB for BSPT threads manufactured by Potter Electric Signal Company.
Additional information for Engineers
Click here to view more info about the VS-SP and VS-SPB.
To view updated tracking on your order, please enter your customer purchase order number.
Please allow at least 24 hours from the time of order for shipping information to be available. For more information or questions about tracking, contact customer service at 800-325-3936.