Have a question, comment, or request? Send us a message!
Hours: 8:00am - 5:00pm CDT
13723 Riverport Drive
St. Louis, MO 63043
1609 Park 370 Place
St. Louis, MO 63042
We are excited to introduce our new training hub, Potter Academy. Through Potter Academy, you will be able to access hundreds of bite sized self-paced training modules, earn CEUs, and deepen your industry and product knowledge – all for free!
Remembering Steve Schilb
We are sorry to hear of the passing of Steve Schilb, longtime employee of Harrington Signal and Potter Electric. …
Potter Announces the PAD300 D-TECT Addressable Sensors and Bases
Potter’s expanded line of D-TECT Sensors and bases have been designed from the ground up with unmatched …
What People Are Saying About Working With Potter
The Model VSG is a flexible vane type of waterflow switch for use in wet pipe water mist systems where a low flow for alarm is required. It is designed for installation in sections of 2 to 4 inch (50mm to 100mm) stainless steel or brass pipe with wall thickness indicated inthe product datasheet (see "Nominal OD and Wall Thickness").
The unit may also be used as a sectional waterflow detector on large systems.
The unit contains an output relay and an adjustable electronic retard. The relay is actuated when a flow of 3 gallons per minute (11,4 LPM) or more occurs downstream of the device. The flow condition must exist for a period of time necessary to overcome the selected retard period.
Codes & Approvals:
Low Flow Waterflow Alarm Vane Switch With Electronic Retard: UL, ULC Listed CSFM Approved waterflow alarm switches shall be furnished and installed at each sprinkler system connection to the wet pipe main where indicated on the drawings, and as required by NFPA Standards. Waterflow switches shall be capable of operation in system pressures up to 450 PSI, maximum surges of up to 18 FPS and alarm activation at 3 GPM. Switch configuration shall consist of two sets of single pole double throw (S.P.D.T.) Form C synchronized sets of contacts rated at 2A, 125 VAC and 2A, 30 VDC. Switch enclosure shall meet NEMA 4 rating and shall be equipped with an electronic, instantly recycling, adjustable retard with a 0-90 second switch selectable range. Power for the operation of the switch shall be 120 VAC or 24 VDC as required. Enclosure cover shall be held captive by tamper resistant screws or supervised for removal by a cover tamper switch. Flow switch saddles shall be corrosion resistant by means of a factory installed non-corrosive insert. Waterflow alarm vane switch shall be Model VSG manufactured by Potter Electric Signal Company.
Click here to view more info about the VSG
For additional questions, contact customer service: firstname.lastname@example.org, or tech support: email@example.com
To view updated tracking on your order, please enter your customer purchase order number.
Please allow at least 24 hours from the time of order for shipping information to be available. For more information or questions about tracking, contact customer service at 800-325-3936.