Potter Global Technologies celebrates its 125 years in the fire and life safety industry. The …
Analog Addressable Duct Detector
The PAD200-DUCT is designed and built to meet all local requirements, as well as the NFPA regulations regarding duct smoke detectors. Air sampling is accomplished by two tubes which protrude into the duct. An exhaust tube of one standard length (7”) is supplied in the installation kit with the smoke duct unit. Once the duct width has been determined the air intake sampling tubes must be ordered. Sampling tubes are supplied in three standard lengths: 2.5 ft., 5 ft., and 10 ft. and cut to size to fit the duct. Mounting the duct smoke unit is accomplished by the use of a template and 2 sheet metal screws, which are provided. Mounting can be achieved without the removal of the clear cover which is secured by 4 capture screws.
Enhanced sensor technology allows the PAD200 Detector Series to comply with the new UL 268 7th edition standards while bringing customers an even higher standard in smoke detection.
Documents & Resources
Potter Academy Training
This product is featured in the Potter Academy training hub. To get started, click a course below or to learn more about Potter Academy, click here.